|Deep Creek||Trepanier Creek||Lake Pumps|
Dec 10 2014
Dec 10, 2014
Switched off June 03, 2014
See Trepanier NTU.
The Lake source consists of two large duty pumps and one small jockey pump When the large pump runs (once/twice a day for approximately 20 minutes to top up the Cousins Road reservoir), the flow is so high that the required contact time to inactivate giardia to the 99.99% treatment objective is not met. As a result, IHA recommended that a Water Quality Advisory be instituted while the Okanagan Lake Pumps are in use.
|GOOD||Less than 1 NTU|
|FAIR (Water Quality Advisory)||1 - 5 NTU|
|POOR (Boil Water Notice)||Greater than 5 NTU|
WATER QUALITY ADVISORY: While the associated health risks are minimal, Interior Health recommends that children, the elderly, people with weakened immune sysems, and anyone seeking additional protection drink boiled water or a safe alternative until further notice. For those at-risk populations, water intended for drinking, washing fruits or vegetables, making juice or ice, or brushing teeth should be boiled for one minute.
BOIL WATER NOTICE: Interior Health recommends that all customers drink boiled water or a safe alternative until further notice. Water intended for drinking, washing fruits or vegetables, making juice or ice, or brushing teeth should be boiled for one minute.
For more info contact the District of Peachland at 250.767.2647 or 250.767.2108 or www.interiorhealth.ca
Spring Runoff and turbidity (discoloured water) occurs annually April to June. Water that looks cloudy or brownish can be expected. Check the Turbidity Report above for information on your water quality. You may choose to leave your drinking water in the fridge to allow it to settle.
A check of your household water filters during this time would be advised as extra fine filters cannot cope if silt is present.